No. Conduit should be stopped just short of the box.
The top of the elbow must be 6″ from the pole..
If the service is being supplied from a utility pole, the member is required to supply 1-10′ section of SCH 80 PVC and 2-10′ sections of SCH 40 PVC to be left near the base of the pole for installation by the power company up the pole.
Yes, contact the power company and a representative will come and inspect the ditch and conduit. The representative will place a white sticker on the meter panel with a pass or fail notice.
Yes, There are three types. Overhead only, Underground only, and Overhead/Underground combination bases. However, combination boxes are not recommended for Underground installations because of their limited wire space.
No, We will not set a meter without a final inspection or in some instances a non occupancy permit shall be allowed from the local electrical inspector.
We offer a variety of lighting products including decorative colonial, cobra head, directional floodlights, and security lights. We can customize plans to fit any lighting need.